Carbon fiber components disking cabin
Disking cabin with aspiration and filtration system
- Type of system: Disking cabin for carbon fiber components
- Air flow: 30,000 m³/h grate section; 8,000 m³/h bench section
- Filter type: Cartridge filter mod. ATEX Aircompact. Immission of heated air into the cabin with CTA.
- Fan: PR 900 to 37 kW; PRM 450 to 5.5 kW
A discing cabin was installed as follows: an 800 mm wide tank has been made where the piping and sector uptake hoppers with manual dampers for flow regulation and reduction have been placed. The opening was closed with suitable grate it has to support and reinforced with supporting pillars. The cabin walls are made of 80/100 mm thick panels, suitable for delimitation and soundproofing. The suction through the grate is carried out by a high performance centrifugal electrical fun. The filtration is done through a cartridge filtration system with pneumatic cleaning. The purified air is expelled through chimney equipped with a sampling inlet positioned in accordance to the regulation. In the upper part of the room a ceiling filtering system and an air intake plenum have been installed so as to create a vertical flow to drop dust. The forced air induction into the cabin takes place through a gas condensing generator with 31.000 m³/h air flow. The system is completed with an electrical panel equipped with inverter, general regulation, valves and control instruments, galvanized sheet pipe, galvanized outside air inlet pipe, air distribution panels.
Next to the cabin, a new cabin has been installed containing two POLIJET suction benches for the trimming of small pieces. The 1.500 mm benches are each equipped with cartridges and compressed air cleaning. The suction from the benches is carried out by a high performance centrifugal fan.
VOC aspiration and filtration system with Thermal Oxidizer
For the aspiration and filtration of VOC deriving from a paint machine, the following system has been realized.
Air aspiration and treatment system with bio-filtration
Extraction and air treatment system from storage and treatment areas of biological sludge, flow rates up to 70,000 m³ / h.
Aspiration and filtration system for coal boilers fumes
For smoke collection of three coal-fired boilers 3 AIRCOM sleeves filters were installed with demister, with a total treated air flow of 185,500 m3 / h.